Your Coronado Heating and Air conditioning Experts
Dependable heating and air conditioning services in Coronado.
Precision Temperature has been providing heating and air conditioning installation, repair, and maintenance to Coronado residents since 1987.
Heating and AC Services You Can Trust
Even the mild temperatures of Coronado can spike in the summer and dip low in the winter. When you need your heating and air conditioning the most you don’t want to find yourself without a properly functioning system.
Regular HVAC maintenance can help keep your unit in tip top shape and ready to provide your family with the comfort you want when you need it most.
At Precision Temperature, we are committed to providing high quality heating and air conditioning services so you and your loved ones can stay safe and comfortable all year long. We are here for all of your heater repairs, AC installations, tune ups and more.
HVAC Solutions for Coronado
- AC Installation and Replacement
- Furnace Repair and Maintenance
- Emergency Services
- Air Conditioner Repair
- Heat Pump Services
- HVAC Maintenance
- Ductless Air Conditioning
- Duct Cleaning Services
for Coronado, CA
Repaired leak on a reach in fridge for Clayton's Coffee on Coronado. t
Checked reach in, need to replace Freon lines
Installed temperature controller in baker's fridge. t
Leak search and repair
Checked condensation leak on a reach-in cooler
Fixing a reach in fridge for a commercial customer. Replaced the evaporator fan motor.
Installed new door hinges on a beverage air two door cold table at Clayton’s Mexican take out.
Reach in freezer not reaching temperature. Found the hinges to be broken on the right hand door of the reach in part of the cold table not allowing the cooler to keep good temperature. I have ordered the hinges. Will return to replace once they come in.
Replaced a cold control on a true reach in freezer at Clayton’s dinner
Reach in refrigerator not cooling. Found evaporator coil to be iced up. Pressures were low. Added refrigerant to system. Unit working now.
Walk in freezer and walk in cooler not reaching temperature. Thermostat not set properly. Reset thermostat. condenser dirty, cleaned with coil cleaner. evaporator frozen solid across, 6 “ thick ice! de iced it. recharged with refrigerant. note- digital control box was loose and signs of board getting wet- may be causing malfunctioning.
Walk in freezer not cooling. Dirty coils, cleaned indoor coils, recharged with refrigerant.
On arrival I noticed the freezer was at room temperature. Found the unit to have no refrigerant. Leak tested unit and found a leak on the evaporator coil. The leak is non repairable. Submitted quote for replacement.
Repair on Beverage Air freezer, leak on evaporator, unit needs replacement. Submitted quote for approval.
Evaporator temp sensor was bad in walk in freezer. Replaced p2 sensor and ran wire through evaporator cover.
Our friendly and knowledgeable staff is ready to handle all of the HVAC needs of homeowners in the Coronado, CA area. For San Diego’s trusted heating and air conditioning experts, call Precision Temperature at (619) 588-5321 today.