As a leading provider of residential and commercial HVAC services in Escondido, Precision Temperature offers high quality heating and air conditioning repair and maintenance services.
With a team of fully trained and certified technicians, we can service any make and model of air conditioner, furnace, ducting, mini-split, walk-in freezer, ice makers, and many other HVAC and refrigeration related equipment.
Any residents or business owners in Escondido know that the climate swings can be a serious challenge and having well performing HVAC equipment is essential.
Whether it is the summer heat that causes you to to crank up the ac, or the winter chill that turns your attention to heating, proper maintenance to keep your unit in peak condition should be your main priority.
The scope of this work is often outside the realm of DIY, and so you’ll need to turn to qualified HVAC contractors.
At Precision Temperature, all of our HVAC technicians are licensed and insured to perform repairs, service, installations, and regular maintenance on all makes and models of heating and cooling equipment.
Is your home or property ready for the upcoming season? Have you had the heating or cooling systems serviced recently?
Call Precision Temperature today at 619-588-5321 to schedule an appointment and get your systems running efficiently in Escondido, CA.
Gym unit not blowing cold air. Inspected wiring and found that the thermostat wire had been cut when the drywall was cut. Repaired the thermostat wire. Started the unit and tested. Unit is operating normally at this time.
Replaced a condenser fan motor
A/C – Alarm is going off when client turns system on. Alarm stops when system is shut off. Reset alarm. Sensor and sensor filters are dirty for the smoke detector. Cleaned filter and sensor, and tested system again. Alarm did not start. Cleaned return grills on lobby unit per customer request.
Replaced pressure control
Tenant informed me that system would run for like 2 hrs and shut off. Checked drain line And water pump and safety switch. They were all working properly. Filter was good evap coil was clean and blower was pulling proper amps. Proceeded to outside unit. Found condenser coil dirty went ahead and cleaned it. Hooked up gauges and found pressures to be low. Indicating there was a leak. Repaired leak. After leak was gone adjusted charge to proper pressures. Everything works now.
Replaced Variable Air Volume Box on supply side of ducting. Airflow going to store was being controlled by an electric damper controlled by a Honeywell 3000 Thermostat. Motor of electric damper was seized. Also replaced existing 115 Volts with 24 Volts transformer.
Replaced old system with a new 2 ton Goodman heat pump and air handler. Placed new condenser, installed new disconnect and electrical whip. Installed a new Honeywell T4 thermostat.
Check out these real reviews from our real customers. We also have a 5-star rating on Yelp!
Precision Temperature, thank you for your honesty and integrity. The level of service I received was first-class..
The estimator and his crew did an excellent job replacing our heater and a/c unit with attention to detail. We would highly recommend his service to others.
The staff treated me with dignity and respect, and made sure I was thoroughly satisfied. I highly recommend Precision Temperature for any of your Heating and Air Conditioning needs.